Solenoid valves are located in three parts as dispenser, system and filler. When the solenoid is energized, it allows air passage and opens the pneumatics. When the energy is cut off, the air will pass and the pneumatics will close and work will stop.
When pressed in any danger that may reach the stations, the button closes the entire system by locking itself. The emergency stop panel can be distinguished by emergency stop, dispenser emergency stop, field emergency stop and four records by coding the name in the specified position. When the emergency stop is pressed, the entire system is turned off and the siren begins to sound in the alarming process. When the resulting hazard is controlled, the emergency stop is removed and the system is reset to return to system operation mode.
Dead Man Button
When the dead man button comes to supply the tanker, the tanker driver reads the tom key registered on the board and selects the tank he has not replenished. After the filling permit is given, the dead man button on the tank is opened and the system starts to fill and the filling is started by providing air flow to the existing pneumatic valve. It is necessary for the driver to make the drop of the dead man button during the period determined so that the driver does not leave the tank area during the supply. If the button is not pressed within the set time, the filling is automatically canceled. The button is functioning as a pushbutton to prevent the button from being pressed and held...
Gas detectors must have at least three TSE 11939 standard devices in each case to receive one stationary, one mobile and one dispenser in the tank. Detectors detect gas escapes and switch the system to alarm mode and shut down the entire system.
Level indicators are parts of the system that allow you to see the tank levels on the pan and tank.
LPG Stock Tank
Equipment to store LPG in stations. The volume of 10 m3 diameter 2300mm and 1600mm is more preferred.
Before starting the tanker supply, the tanker plug must be take into the tanker socket on the tank area.Tanker socket; It is used to interrupt transfer to LPG Tank when alarm is detected and to actively operate the earthing system.
Cathodic protection is providing to prevent the corrosion of the tank and the underground pipeline (SCH) and to protect their life.
Sabit Referans Elektrodu eng
Copper-copper sulphate reference electrode used in potential measurement and buried under the ground constantly is manufactured as long life (15 years) in special ceramic pot.
Dispenser is the equipment that provides sales according to the determined liter / price vehicle supply.